Made available by
Touch N' Go Systems, Inc., and the
Law Offices of James B. Gottstein.
You can also go to The Alaska Legal Resource Center or search the entire website search.
(a) No utility may interconnect with a qualifying facility that fails to conform to the edition of the National Electrical Code adopted in AS 18.60.580 .
(b) No utility may interconnect with a qualifying facility that does not provide a means of disconnecting with provision for padlocking in the open position by the utility. This device, or a supplementary device, must be capable of switching under full load conditions and must be clearly labeled and accessible to utility personnel.
(c) No utility may interconnect with a qualifying facility that does not provide overcurrent protection of adequate interrupting capacity and design, in conformance with the utility's overcurrent practices for similar feeders and loads, for the feeder serving as the intertie to the utility system. Automatic reclosing by the qualifying facility is prohibited unless the facility has received prior approval from the utility as not posing a threat to life or property.
(d) A utility shall provide overcurrent protection in accordance with the utility's overcurrent practices for similar feeders and loads for the feeder extension serving as the intertie to a qualifying facility.
History: Eff. 1/1/87, Register 100
Authority: AS 42.05.141
Note to HTML Version:
The Alaska Administrative Code was automatically converted to HTML from a plain text format. Every effort has been made to ensure its accuracy, but neither Touch N' Go Systems nor the Law Offices of James B. Gottstein can be held responsible for any possible errors. This version of the Alaska Administrative Code is current through June, 2006.
If it is critical that the precise terms of the Alaska Administrative Code be known, it is recommended that more formal sources be consulted. Recent editions of the Alaska Administrative Journal may be obtained from the Alaska Lieutenant Governor's Office on the world wide web. If any errors are found, please e-mail Touch N' Go systems at E-mail. We hope you find this information useful. Copyright 2006. Touch N' Go Systems, Inc. All Rights Reserved.
Last modified 7/05/2006