Made available by
Touch N' Go Systems, Inc., and the
Law Offices of James B. Gottstein.
You can also go to The Alaska Legal Resource Center or search the entire website search.
(a) An automatically fired steam boiler must be equipped with an automatic low-water fuel cutoff.
(b) An automatically fired hot water heating or hot water supply boiler that exceeds an input of 400,000 Btu per hour must be equipped with an automatic low-water fuel cutoff or a loss of flow switch, as appropriate for the heater or boiler.
History: Eff. 6/21/84, Register 90; am 12/17/99, Register 152
Authority: AS 18.60.180
Note to HTML Version:
The Alaska Administrative Code was automatically converted to HTML from a plain text format. Every effort has been made to ensure its accuracy, but neither Touch N' Go Systems nor the Law Offices of James B. Gottstein can be held responsible for any possible errors. This version of the Alaska Administrative Code is current through June, 2006.
If it is critical that the precise terms of the Alaska Administrative Code be known, it is recommended that more formal sources be consulted. Recent editions of the Alaska Administrative Journal may be obtained from the Alaska Lieutenant Governor's Office on the world wide web. If any errors are found, please e-mail Touch N' Go systems at E-mail. We hope you find this information useful. Copyright 2006. Touch N' Go Systems, Inc. All Rights Reserved.
Last modified 7/05/2006